How to improve temperature measurement with ventilation systems
If you have it installed so that it is flush mounted, there is often a negative pressure in some rooms and positive pressure in other rooms, especially in airtight apartments or modern buildings, and this can cause the Powered Room Thermostat to have air passing through it which is not representative of the air in the room. This air passing past the sensor can disrupt the algorithm in the thermostat which is used to calculate the air temperature in the room
Fix this by surface mounting the Powered Room Thermostat or factory resetting the Powered Room Thermostat (see below) to re-start the learning algorithm
Problems with the temperature being read as too high when not heating
The LED screen if left on for long periods of time can generate heat and this can affect the temperature that the Powered Room Thermostat experiences
Reduce the brightness of the LEDs or turn off the LEDs using this article.
To Factory Reset the Powered Room Thermostat
- See this article.